- Trending Categories
- Data Structure
- Operating System
- C Programming
- Selected Reading
- UPSC IAS Exams Notes
- Developer's Best Practices
- Questions and Answers
- Effective Resume Writing
- HR Interview Questions
- Computer Glossary
- Who is Who
Three Phase Induction Motor Starting Methods
There are two types of three phase induction motors viz. squirrel cage motor and slip ring motor. Both have different methods of starting, let see each of these one by one.
Squirrel Cage Induction Motor Starting Methods
The following four methods are available for starting squirrel cage motors −
Direct On-Line (D.O.L.) Starting
As the name suggests, the induction motor is started by connecting it directly to three-phase supply. In this method, the motor draws a high starting current (about 4 to 7 times of the rated current) and at low power factor. Therefore, DOL starting is suitable for relatively small motors (up to 10 kW).
Stator Resistance Starting
In this method, external resistance is connected in series with each phase of the stator winding during starting. The external resistance causes voltage to drop across it so that reduced voltage available across the motor terminals. Hence, the starting current is reduced. The starting external resistances are gradually cut out in steps from the stator circuit, as the motor accelerates. When the motor attains the rated speed, the starting resistances are completely cut out and full line voltage is applied across the motor terminals.
This method has two drawbacks. First, the reduced voltage during starting reduces the starting torque and hence increases acceleration time. Secondly, a lot power is wasted in the starting resistances.
In this method, an autotransformer is used to reduce the starting voltage of the induction motor. The tapings of the autotransformer is so set that when it is in the circuit, 60 to 80 % of the line voltage is applied to motor during starting and then connecting it to the full-line voltage as the motor attains a sufficient speed.
At the instant of starting, the change-over switch is connected to ‘Start’. This supplies the reduced voltage to the motor through the autotransformer. Consequently, the starting current is limited to safe value. When the motor attains about 80% of rated-speed, the change-over switch is now thrown to ‘Run’. This removes the autotransformer from the circuit and full line voltage is applied across the motor terminals.
The autotransformer starting has many advantages such as low power loss, low starting current etc. This method is used for large motors over 25 hp.
In star-delta starting method of squirrel cage induction motor, the motor started in star and run in delta, i.e. the stator winding of the motor is designed for delta operation and is connected in star during starting. When the motor attains sufficient speed, the connections are changed to delta.
The six leads of stator winding of the motor are connected to a change-over switch. At the time of starting, the change-over switch is switched to ‘Star’ which connects the stator windings in star. Thus, each phase gets V/√3 volts, where V is the three phase line voltage. This reduces the starting current. When the motor attains 80% of rated speed, the changeover switch is switched to ‘Delta’ which connects the stator windings in delta. Now, each phase gets full line voltage.
The principle disadvantage of this method is large reduction in stating torque due to reduced voltage in the star connection at the instant of starting. The star-delta starting is used for medium size motors up to 25 hp.
Slip Ring Induction Motor Starting Methods
The following four methods are used to start a slip ring induction motor −
Direct On-Line (D.O.L.) Starting
The DOL starting, Stator-Resistance starting and Autotransformer starting are same as for the squirrel cage induction motor (as discussed above)
In industrial applications, the slip ring induction motor are mainly started using rotor-resistance method.
Rotor Resistance Starting
In this method, a star connected variable resistance is connected in the rotor circuit through slip-rings. The full voltage is applied to the stator windings.
At the instant of starting, the handle of variable resistance (rheostat) is set to ‘OFF’ position. This inserts maximum resistance in series with the each phase of the rotor circuit. This reduces the starting current and at the same time starting torque is increased due to external rotor resistance.
As the motor accelerates, the external resistance is gradually removed from the rotor circuit. When the motor attains rated speed, the handle is switched in the ‘ON’ position, this removes the whole external resistance from the rotor circuit.
- Methods of Starting Single-phase Induction Motor
- Starting Torque of 3-Phase Induction Motor; Torque Equation of 3-Phase Induction Motor
- Running Torque of Three-Phase Induction Motor
- Three Phase Induction Motor – Working Principle
- Three-Phase Induction Motor Torque-Speed Characteristics
- Rotating Magnetic Field in Three-Phase Induction Motor
- Rotor Resistance Starter in Three-Phase Induction Motor
- Construction of 3-Phase Induction Motor
- Ratios of Full-Load, Starting and Maximum Torques of 3-Phase Induction Motor
- Two-Phase AC Servo Motor and Three-Phase AC Servo Motor
- Starting Methods of Synchronous Motor
- Torque Slip Characteristics of 3-Phase Induction Motor
- Difference between Single-phase and Threephase Induction Motor
- Split-Phase Induction Motor – Operation and Characteristics
- Rotating Magnetic Field in a 3-Phase Induction Motor