- Trending Categories
- Data Structure
- Networking
- RDBMS
- Operating System
- Java
- MS Excel
- iOS
- HTML
- CSS
- Android
- Python
- C Programming
- C++
- C#
- MongoDB
- MySQL
- Javascript
- PHP
- Physics
- Chemistry
- Biology
- Mathematics
- English
- Economics
- Psychology
- Social Studies
- Fashion Studies
- Legal Studies

- Selected Reading
- UPSC IAS Exams Notes
- Developer's Best Practices
- Questions and Answers
- Effective Resume Writing
- HR Interview Questions
- Computer Glossary
- Who is Who

# Saturated and Unsaturated Synchronous Reactance in Synchronous Generator

## Unsaturated Synchronous Reactance

At low excitations, the open-circuit characteristic (OCC) of an alternator coincides with the air-gap line, thus, the synchronous impedance of the alternator is constant and this value of the synchronous impedance is known as *linear* or *unsaturated synchronous impedance*.

The **unsaturated synchronous reactance** (denoted by *X _{su}*) can be obtained from the air-gap line voltage and the short-circuit current of the alternator for a particular value of the field current.

**Note** – *SCC is the short-circuit characteristic*.

From the characteristics, the unsaturated synchronous impedance is given by,

$$\mathrm{𝑍_{𝑠𝑢} =\frac{𝐸_{𝑎𝑑}}{𝐼_{𝑎𝑏}}= 𝑅_{𝑎} + 𝑗𝑋_{𝑠𝑢}}$$

If the armature resistance of the alternator is neglected, then the unsaturated synchronous reactance is given by,

$$\mathrm{X_{𝑠𝑢} =\frac{𝐸_{𝑎𝑑}}{𝐼_{𝑎𝑏}}}$$

## Saturated Synchronous Reactance

With the increasing excitation, the effect of the saturation decreases the value of synchronous impedance and hence the values of the synchronous impedance beyond the linear part of the OCC are known as *saturated synchronous impedances*. The values of the saturated synchronous impedance are not constant but vary with the excitation and the power factor of the alternator on load.

The approximate value of the synchronous reactance varies with the degree of saturation of the open-circuit characteristic. Hence, the value of the synchronous reactance to be used in a given problem should be one calculated at the approximate load on the alternator. If the alternator is connected to the infinite bus, then its terminal voltage remains the same at the bus value.

If the field current of the machine is changed, the excitation voltage will change – not along the open-circuit characteristic, but along the line Oc *(refer the above figure)* that is known as *modified air-gap line.* This modified air-gap line represents the same magnetic saturation level as that corresponding to the operating point ‘c’. Therefore, the **saturated synchronous reactance** at the rated voltage is obtained as follows −

$$\mathrm{𝑍_{𝑠\:(sat.)} =\frac{𝐸_{𝑎𝑐}}{𝐼_{𝑎𝑏}}= 𝑅_{𝑎 }+ 𝑗𝑋_{𝑠(sat.)}}$$

If the armature resistance is neglected, then the saturated synchronous reactance is given by,

$$\mathrm{𝑋_{𝑠\:(sat.)} =\frac{𝐸_{𝑎𝑐}}{𝐼_{𝑎𝑏}}}$$

- Related Articles
- What is Synchronous Reactance & Synchronous Impedance?
- Synchronous Generator – Construction and Working Principle
- Prime-Mover Governor Characteristics (Synchronous Generator)
- Armature Reaction in Alternator or Synchronous Generator
- Cooling of a Synchronous Generator or Alternator
- EMF Equation of Synchronous Generator or Alternator
- Voltage Regulation of Alternator or Synchronous Generator
- Power Input of Synchronous Generator or Alternator
- Power Output of Synchronous Generator or Alternator
- Synchronous Generator – Zero Power Factor Characteristics and Potier Triangle
- Hydrogen Cooling of a Synchronous Generator or Alternator
- Power Flow Transfer Equations for a Synchronous Generator
- Operation of Synchronous Generator with an Infinite Bus
- Equivalent Circuit and Phasor Diagram of Synchronous Generator or Alternator
- Difference between Cylindrical Rotor and Salient Pole Rotor Synchronous Generator