- Trending Categories
- Data Structure
- Networking
- RDBMS
- Operating System
- Java
- iOS
- HTML
- CSS
- Android
- Python
- C Programming
- C++
- C#
- MongoDB
- MySQL
- Javascript
- PHP

- Selected Reading
- UPSC IAS Exams Notes
- Developer's Best Practices
- Questions and Answers
- Effective Resume Writing
- HR Interview Questions
- Computer Glossary
- Who is Who

# How Does a Three-Phase Autotransformer Function?

A *three-phase star-connected autotransformer* is shown in the figure. The three-phase autotransformers are used for small ratios of transformation.

In practice, the star connected three-phase autotransformers are used and the delta connected autotransformers are avoided. The primary application of three phase autotransformers is for interconnecting two power systems of different voltage levels such as 66 kV to 132 kV power systems, 110 kV to 220 kV power systems, 220 kV to 400 kV power systems etc.

## Numerical Example

A three-phase star-connected autotransformer supplies a balanced three-phase load of 100 kW at 380 V and at 0.85 power factor lagging. If the supply voltage is 440 V, Calculate the winding currents as well as the input and output line currents. Neglect the excitation current and the internal voltage drops in the transformer.

**Solution**

The connection diagram of the given autotransformer is shown in the figure.

The three-phase power is given by,

$$\mathrm{𝑃 = √3\:𝑉_{𝐿}\:𝐼_{𝐿}\:cos\:φ}$$

$$\mathrm{∴𝐼_{𝐿}=\frac{𝑃}{√3\:𝑉_{𝐿}\:cos\:φ}=\frac{100\:×\:10^{3}}{√3×\:380\:×\:0.85}}$$

$$\mathrm{\Rightarrow\:𝐼_{𝐿}= 178.75\:A}$$

Thus, the *output line current* of the given three-phase autotransformer is 178.75 A.

As the losses are neglected, therefore,

$$\mathrm{Input\:VA\:per\:phase\:(𝑉_{𝐻}𝐼_{𝐻}) = output\:VA\:per\:phase(𝑉_{𝐿}𝐼_{𝐿})}$$

$$\mathrm{\Rightarrow\:\frac{440}{√3}× 𝐼_{𝐻}=\frac{380}{√3}×\:𝐼_{𝐿}}$$

$$\mathrm{\Rightarrow\:𝐼_{𝐻}=\frac{380}{440}× 178.75 = 154.37\:A}$$

Thus, the *input line current* of the given three-phase autotransformer is 154.37 A.

Now, the currents flowing from neutral point (N) to tapping points A, B and C are given by applying KCL at respective tapping point, thus,

$$\mathrm{𝐼_{𝑁𝐴}= 𝐼_{𝑁𝐵}= 𝐼_{𝑁𝐶}= 𝐼_{𝐿}\:−\:𝐼_{𝐻}= 178.75\:−\:154.37 = 24.38\:A}$$

Therefore, the *currents flowing in the windings* of the given transformer are equal to 24.38 A.

- Related Questions & Answers
- Three-Phase Electric Power
- Harmonics in Three Phase Transformers
- Advantages of Three-Phase System
- Basics of Three-Phase Electricity
- Working Principle of a Three-Phase Transformer
- Three Phase Induction Motor Starting Methods
- Three-Phase to Twelve-Phase Transformers: Circuit Diagram and Phasor Diagram
- Two-Phase AC Servo Motor and Three-Phase AC Servo Motor
- Running Torque of Three-Phase Induction Motor
- Sudden Short Circuit of Three-Phase Alternator
- Three Phase Induction Motor – Working Principle
- Three-Phase Induction Motor Torque-Speed Characteristics
- Types of AC Generators – Single Phase and Three Phase AC Generator
- Rotating Magnetic Field in Three-Phase Induction Motor
- Rotor Resistance Starter in Three-Phase Induction Motor